Electrical Repairs at Cross Fit
A Cross Fit Location had Many electrical issues corrected. Many of the recessed can lights in the ceiling were inoperative and improperly wired. All of the lights were repaired in the commercial building, a couple lights were even added. Poor wiring in the bathrooms were corrected,
The bathroom exhaust fan/lights were also inoperative, plus the vent pipes were disconnected in the attic area.
The electric water heater didn't work as well, The wiring was corrected and the tank work fine now. The tank was also improperly strapped for seismic/earthquake.